Tripp Lite Smart Pro
The Tripp Lite Smart Pro delivers amazing voltage regulation, surge suppression, plus professional class battery support for your different computers, network workstations, home entertainment systems and media centers. It caters as an outstanding power support for your devices during power failures or surges. It is even helpful in giving an ample power for your systems to be shut down properly, preventing critical data loss. This device comes with 8 UPS battery-supported outlets for you to plug in your devices stably. It is also ready to regulate power outages or overvoltage from 75V to 147V back to usable levels. A set of reliable phone/network protection jacks are also present to keep your DSL phone line or network Ethernet connection from probable surges. And of course the valuable LCD Display shows input voltage, battery capacity, and a variety of operating conditions for easy viewing of the Rackmount UPS Battery Backup’s status. Worry no more about equipment damages during sudden blackouts with the Tripp Lite Smart Pro today.
What It Is And Why You Need It:
A Closer Look
Power Protection Specifications
|Power Protection Type||Rackmount UPS Battery Backup|
|Connector Type||RJ45 Ethernet|
|Input Connection Type||NEMA 5-15P|
|Recommended Electrical Service||120V, 15A|
|Volt Amps||1500 VA|
|Full Load Run Time||3.5 minutes|
|Half Load Run Time||13 minutes|
|Battery Recharge Rate||2-8 hours to 90%|
|Battery Run Time||1-30 Min|
Protection and Filtering
|Surge Energy Capacity||480 Joules|
|Short Circuit||10A circuit breaker|
|Connected Equipment Warranty||$250,000|
Status Indicators / Controls
|LEDs||Battery Power Status|
|Voltage Regulation Operation|
|Switches||Alarm Cancel / Self Test Button|
|Main Power Button|
|Serial||1 DB9 Communication Port|
|Software Included||Power Alert|
|Operating Temperature||5 to +122 degrees Fahrenheit / -15 to +50 degrees Celsius|
|+32 to +104 degrees Fahrenheit / 0 to +40 degrees Celsius|
|Dimensions||43.8" x 8.9" x 26.7"|
Have an opinion on this product that you would like to share? If, so please take a few moments to write your rating and review.Write your own review
Sorry Not Great
I hate to spoil your party, but this unit has not met with my expectations, three times. 1. Unit got fried by Lightning. 2. Unit smelled bad. Returned it as it made me ill. Marketing says they use a preservative to store components during manufacture and shipping. 3. Unit 3 Bad fan. 4. If Unit 4 is bad I am returning that and asking for a refund. They are helpful, but THIS PRODUCT IS NOT the Best for what you pay.
I really like the real-time voltage display. You begin to appreciate how often this unit is working to provide stable power to your sensitive electronics. No fuss, no muss operation. Solid build construction. Bought a 2nd unit and would have no hesitation buying another one if needed.
Great Unit For $
I compared MANY units and this one kept creeping to the top of the list for features and price. I ordered 2 units. Units perform well in my business environment.
Right product - Right Price
Hits the sweet spot for price and performance. My 5 yr old APC unit went BLAM; replaced it with Tripp Lite. Unit provides UPS for almost 15 TB of NAS on my network. Held up like a trooper during several power sags and outages.
I have had this unit for 2 months. No problems, easy to set up. I live in the 'sticks' and power surges and brief outages are frequent. I have been an APC user for years, but hate the beeping. Haven't heard this one beep yet, and there has been outages. It just quietly does it's job an minds its own business. Like the software features. So far has been doing it's job. I like the digital read-out too. Was surprised to see how much power really changes.
11 Harbor Park Drive,
Port Washington, NY 11050.